[CCMC 14138-R] CCMC Canadian code compliance evaluation
From: National Research Council Canada
Duka Technologies Inc.
400 Applewood Cres.
|Product name:||Duka Open Cell SPF|
|Code compliance:||NBC 2015|
In most jurisdictions this document is sufficient evidence for approval by Canadian authorities.Learn more about CCMC recognition Look for the trusted CCMC mark on products to verify compliance.
Code compliance opinion
It is the opinion of the Canadian Construction Materials Centre that the evaluated product, when used as a thermal insulation in accordance with the conditions and limitations stated in this evaluation, complies with the following code:
National Building Code of Canada 2015
|ID||Code provision||Solution type|
|01-02-01-01-01-b-00||A-220.127.116.11.(1)(b) Code Compliance via Alternative Solutions||Alternative|
|18.104.22.168. Insulation Materials||Acceptable|
The above opinion is based on the evaluation by the CCMC of technical evidence provided by the evaluation holder, and is bound by the stated conditions and limitations. For the benefit of the user, a summary of the technical information that forms the basis of this evaluation has been included.
Product nameDuka Open Cell SPF
The product is a Type 1, spray-in-place, low-density, semi-flexible plastic foam insulation that has an open-cell structure. The product consists of
- Duka Open Cell SPF part A isocyanate, and
- Duka Open Cell SPF part B resin,
which are mixed on site by a qualified installer using positive displacement equipment in a 1:1 fixed ratio.
The final cured product is yellow and has a density of 6.8 kg/m3. At a thickness of 25.4 mm, the thermal resistance is 0.61 m2·°C/W.
This evaluation is valid only for products produced at the following plant:
|Product name||Manufacturing plant|
|Brantford, ON, CA|
|Duka Open Cell SPF||Product evaluated by the CCMC|
Product evaluated by the CCMC Indicates that the product from this manufacturing facility has been evaluated by the CCMC
Conditions and limitations
The CCMC’s compliance opinion is bound by this product being used in accordance with the conditions and limitations set out below.
- The product must be applied on site by qualified installers trained and approved by Duka Technologies Inc.
- As specified by the manufacturer, the product must be manufactured on site by qualified installers trained and approved by Duka Technologies Inc. with subsequent field auditing of installers by Urethane Foam Consultants (UFC).Footnote (1) UFC is the third-party certification organization specified by Duka Technologies Inc. to certify the training program and provide follow-up inspections of qualified installers who are licensed to spray semi-flexible, urethane-based foam insulation in accordance with the Duka Technologies Inc. Installer’s Manual.
- The product can be installed in new or retrofit constructions. In either case, the product must be installed in open cavities in the following locations in a wood-frame construction that meets the requirements of the NBC 2015 (see Figure 1):
- exterior walls including perimeter joists;
- cathedral ceilings with a vented air space as required by the NBC 2015;
- floors separating living spaces from a garage;
- cantilever overhang floors; or
- interior below-grade foundation walls.
- The building envelope where the product is installed must conform to the requirements of the NBC 2015 for vapour barriers, air barriers and damp proofing (interior below-grade walls).
- For retrofit applications whereby there may be occupants in the unaltered part of the building, the qualified installer must ensure that the spraying area is isolated and negatively pressurized by using an exfiltration rate of 0.3 air changes per hour for at least 1 day. An independent toxicological assessment determined that this ventilation rate must also be in effect for 1 day before occupancy is permitted in the newly insulated suite.
- The sprayed material should completely cover the surfaces between the studs, joists and other framing members. The surfaces to be covered should be clean, dry and not covered in frost, oil, grease, dust or other contaminants. As required in Article 22.214.171.124., Installation of Thermal Insulation, of Division B of the NBC 2015, the insulation must be installed so that there is a reasonably uniform insulating value over the entire face of the insulated area.
- The interior side of the applied semi-flexible polyurethane insulation must be covered with an approved thermal barrier as per Article 126.96.36.199., Protection of Foamed Plastics, of Division B of the NBC 2015.
- The insulation must be kept away from heat-emitting devices, such as recessed light fixtures and chimneys, at the minimum distance required by building regulations and safety codes.
- The maximum in-service temperature of the insulation must not exceed 70°C.
- The product must not be used where it may come in contact with water and must not be installed after its expiry date of 6 months from the date of manufacture.
- The isocyanate and resin components must have their respective containers (i.e., drums) identified with the phrase “CCMC 14138-R.”
- The installation procedure must follow the manufacturer’s instruction manual. A copy of the manual must be available at the job site at all times during the installation for review by the building official.
This evaluation is based on demonstrated conformance with the following criteria:
|Criteria number||Criteria name|
|CCMC-TG-072119.03-15||CCMC Technical Guide for Spray-in-Place, Open-Cell Polyurethane Foam (OPF) Thermal Insulation|
|Thermal resistance at 25-mm thickness||m2·°C/W||Report value||0.61|
|Water vapour transmission for 50-mm thickness||ng/(Pa·s·m2)||> 1400 (Type 1)||1 580|
|Water absorption||%||Report value||17.4|
|Dimensional changes when exposed to:||80°C and ambient RH||% volumetric||min. –15||max. +10||0|
|70°C and 97 ± 3% RH||min. –15||max. +14||–0.1|
|–29°C and ambient RH||min. –1||–||–0.1|
|Emissions: time to occupancy||–||See noteTable footnote (1)||Pass|
|Flame-spread rating (CAN/ULC-S102 and CAN/ULC-S127)||Report value||
|Smoke development||Report value||195|
Use of Canadian Construction Materials Centre (CCMC) assessments
This assessment must be read in the context of the entire CCMC Registry of Product Assessments, any applicable building code or by-law requirements, and/or any other regulatory requirements (for example, the Canada Consumer Product Safety Act, the Canadian Environmental Protection Act, etc.).
It is the responsibility of the user to confirm that the assessment they are using is current and has not been withdrawn or superseded by a later version on the CCMC Registry of Product Assessments.
The National Research Council of Canada (NRC) has evaluated only the characteristics of the specific product described herein. The information and opinions in this evaluation are directed to those who have the appropriate degree of experience to use and apply its contents (such as authorities having jurisdiction, design professionals and specifiers). This evaluation is valid when the product is used as part of permitted construction, respecting all conditions and limitations stated in the evaluation, and in accordance with applicable building codes and by-laws.
This evaluation is provided without representation, warranty or guarantee of any kind, expressed or implied, and the NRC provides no endorsement for any evaluated product. The NRC accepts no responsibility whatsoever arising in any way from any and all use of or reliance on the information contained herein or the use of any evaluated product. The NRC is not undertaking to render professional or other services on behalf of any person or entity nor to perform any duty owed by any person or entity to another person or entity.
Une version française de ce document est disponible.
In the case of any discrepancy between the English and French version of this document, the English version shall prevail.
© His Majesty the King in Right of Canada, as represented by the National Research Council of Canada, 2023
All rights reserved. No part of this publication may be reproduced, stored in a retrieval system, or transmitted in any form or by any means, electronic, mechanical, photocopying, recording or otherwise, without the prior written permission of the CCMC.