[CCMC 14078-L] CCMC Standard compliance evaluation
From: National Research Council Canada
In most jurisdictions this document is sufficient evidence for approval by Canadian authorities.Learn more about CCMC recognition
- Airmetic® SOYA HFO
- Heatlok® SOYA HFO
- Polar Foam SOYA HFO
Ozone-Depleting Substances and Halocarbons Alternatives Regulations (ODSHAR)The evaluation holder attests that this/these product(s) contains a foaming agent that is compliant with the Ozone-Depleting Substances and Halocarbons Alternatives Regulations, which is administrated by Environment and Climate Change Canada (ECCC)
The product is a closed-cell, spray-applied rigid polyurethane foam of medium density. The foam system consists of two components that must be labelled as follows along with “CCMC 14078-L":
- Isocyanate (Component A): “A100” isocyanate; and
- Resin (Component B): “Airmetic® SOYA HFO, Heatlok® SOYA HFO, Polar Foam SOYA HFO” resin.
The two components are mixed on-site by a Huntsman Building Solutions (Canada) Inc. qualified installer (see Qualified installers section) with fixed-ratio positive displacement equipment. The colour of the installed final cured product Airmetic® SOYA HFO and Heatlok® SOYA HFO is green.The colour of the installed final cured product Polar Foam SOYA HFO is peach.
This is a site-manufactured product; it is finished on-site following the spray-application of raw materials produced at the manufacturing plant(s) below.
This evaluation is limited to products produced at the following plant(s):
- Boisbriand, Québec, Canada
This evaluation is based on demonstrated conformance with the following criteria:
|Criteria number||Criteria name|
|CAN/ULC-S705.1-15||Standard for Thermal Insulation - Spray Applied Rigid Polyurethane Foam, Medium Density - Material Specification|
|Product||Minimum site densityTable footnote (1) (kg/m3) [lb/ft3 ]||50 mm design LTTR (m2 ∙C/W)||50 mm WVPTable footnote (2) (ng/(Pa∙s∙m2 ))||Time-to-occupancyTable footnote (3) (hours)|
|Airmetic® SOYA HFO||33.72 [2.1]||1.86||51||25|
|Heatlok® SOYA HFO|
|Polar Foam SOYA HFO|
This is a site-manufactured product whereby Huntsman Building Solutions (Canada) Inc. requires that only specific, qualified installers be authorized to install their proprietary spray-polyurethane insulation in buildings. In accordance with the Huntsman Building Solutions (Canada) Inc. site quality assurance program (SQAP), Caliber Quality Solutions Inc. (Caliber) has been commissioned to license the specified installers and issue the requisite Caliber identification card to them. All specified installers must have a Caliber identification card.
Third-party site auditing of qualified installers
As part of their SQAP, Huntsman Building Solutions (Canada) Inc. also stipulates that site-audit inspections be conducted by site inspectors licensed by Caliber. Upon completion of the site audit, Caliber will report the product’s conformity results and any corrective action required, if necessary, to Huntsman Building Solutions (Canada) Inc. Building officials who would like site-audit inspections to be conducted on specific building sites can contact Caliber at:Caliber Quality Solutions Inc.
Suite 1000, 120 Eglinton Ave. East
Toronto, ON M4P 1E2
The foam insulation is a site-manufactured product.
This evaluation is issued by the Canadian Construction Materials Centre (CCMC), part of the Construction Research Centre at the National Research Council of Canada (NRC). The evaluation must be read in the context of the entire CCMC Registry of Product Assessments and the legislated applicable building code in effect.
The CCMC was established in 1988 on behalf of the applicable regulator (i.e., the provinces and territories) to ensure—through assessment—conformity of alternative and acceptable solutions to regional building codes as determined by the local authority having jurisdiction (AHJ) as part of the issuance of a building permit.
It is the responsibility of the local AHJs, design professionals, and specifiers to confirm that the evaluation is current and has not been withdrawn or superseded by a later issue. Please refer to the website or contact:
Canadian Construction Materials Centre
Construction Research Centre
National Research Council of Canada
1200 Montreal Road
Ottawa, Ontario, K1A 0R6
The NRC has evaluated the material, product, system or service described herein only for those characteristics stated herein. The information and opinions in this evaluation are directed to those who have the appropriate degree of experience to use and apply its contents (i.e., AHJs, design professionals and specifiers). This evaluation is only valid when the product is installed in strict compliance with the stated conditions and limitations of evaluation and the applicable local building code. In circumstances where no applicable local building permit is issued and that no confirmation of compliance ‘for use in the intended field application’ is undertaken, this evaluation is null and void in all respects. This evaluation is provided without representation, warranty, or guarantee of any kind, expressed, or implied, and the NRC provides no endorsement for any evaluated material, product, system or service described herein. The NRC accepts no responsibility whatsoever arising in any way from any and all use and reliance on the information contained in this evaluation with respect to its compliance to the referenced code(s) and standard(s). The NRC is not undertaking to render professional or other services on behalf of any person or entity nor to perform any duty owed by any person or entity to another person or entity.
Une version française de ce document est disponible.
In the case of any discrepancy between the English and French version of this document, the English version shall prevail.
© 2021 Her Majesty the Queen in Right of Canada, as represented by the National Research Council of Canada.
All rights reserved. No part of this publication may be reproduced, stored in a retrieval system, or transmitted in any form or by any means, electronic, mechanical, photocopying, recording or otherwise, without the prior written permission of the CCMC.