[CCMC 12420-R] CCMC Canadian code compliance evaluation
From: National Research Council Canada
|Code compliance:||NBC 2015, OBC 2017|
In most jurisdictions this document is sufficient evidence for approval by Canadian authorities.Learn more about CCMC recognition
Code compliance opinion
It is the opinion of the Canadian Construction Materials Centre (CCMC) that “Enviro-Shield,” when used as a system to install thermal insulation in accordance with the conditions and limitations stated in Section 3 of this Report, complies with the National Building Code (NBC) of Canada 2015:
National Building Code of Canada 2015
|Code provision||Solution type|
|220.127.116.11.(1)(f) Insulation Materials||Acceptable|
|18.104.22.168. Installation of Loose-Fill Insulation||Acceptable|
Ontario Building Code 2017
Ruling No. 03-02-91 (12420-R) authorizing the use of this product in Ontario, subject to the terms and conditions contained in the Ruling, was made by the Minister of Municipal Affairs and Housing on 2003-03-18 (revised 2010-06-22) pursuant to s.29 of the Building Code Act, 1992 (see Ruling for terms and conditions). This Ruling is subject to periodic revisions and updates.
The above opinion is based on the evaluation by the CCMC of technical evidence provided by the evaluation holder, and is bound by the stated conditions and limitations. For the benefit of the user, a summary of the technical information which forms the basis of this evaluation has been included.
The “Enviro-Shield” system is manufactured on the job site. The system comprises three components:
- the thermal insulating product,
- the frame wall construction, and
- the installation method.
The insulating product is loose-fill cellulose insulation produced using the advanced fibre technology system and must bear a CCMC Evaluation Listing number.
The framing consists of conventional 38 mm × 140 mm or 38 mm × 89 mm wood studs or galvanized steel studs spaced at either 400 mm or 600 mm. The insulation is installed behind either a 6 mil CGSB-certified vapour barrier or a woven polypropylene mesh to permit product inspection before closing the wall/ceiling with drywall.
Installing the product in walls consists of piercing the vapour barrier or the mesh near the top of the cavity and lowering the blowing hose into the cavity (see Figure 1). By carefully controlling the filling time and filling pressure with conventional or modified conventional blowing equipment, the cavity can be completely filled to a specified design density of 48 kg/m3 within a tolerance of 10%. Installation for the product in cathedral ceilings is the same as for walls, except that:
- cavities are filled to a minimum specified density of 40.5 kg/m3 ,
- a ventilation system is included (see Figure 2), and
- cavities longer than 3 m must be blown in stages
This is a site-manufactured product; it is finished on site following the pouring or pneumatic installation of raw materials produced at the manufacturing plant(s) below.
This evaluation is valid only for products produced at the following plants:
- Debert, Nova Scotia, Canada
Conditions and limitations
The CCMC’s compliance opinion is bound by this product being used in accordance with the conditions and limitations set out below.
Installation of the loose-fill cellulose insulation system must be limited to basement walls that:
- have an explicit drainage layer on the exterior of the basement wall from ground level to the footing (e.g., semi-rigid dimpled polyethylene products, exterior insulations); or
- have waterproofing on the exterior face of the concrete; or
- have dampproofing on the exterior face, where the concrete is free of defects (any cracks must be sealed to prevent future water entry, whether or not there is evidence of past or current water entry); or
- are not subject to flooding and not situated in areas with a high water table (< 2.5 m from ground surface) or that are susceptible to sewer backup.
Installations on cast-in-place concrete basement walls must not occur until 45 days after casting of the concrete.
The following limitations apply when the system is used with steel studs:
- 25% of the insulating value must be on the outside of the steel studs (i.e., insulative sheathing); and
- the density of the galvanizing coating on the steel studs must be 275 g/m2 or greater.
The system can only be installed in cathedral ceilings that incorporate a ventilation system in accordance with Subsection 9.19.1., Venting, of Division B of the NBC 2015.
- The thermal insulating product must be cellulose insulation produced using the advanced fibre technology and bearing a valid CCMC Evaluation Listing number.
- The blowing equipment used must be any commercially available machine modified according to Thermo-Cell’s instructions.
- The insulation must be kept away from heat-emitting devices such as recessed light fixtures, chimneys, and propane or natural gas sources, at a distance of at least 75 mm or the distance required by the local authority having jurisdiction.
- Pierced vapour barriers must be repaired in accordance with current best trade practice.
- Installation of the “Enviro-Shield” system must be carried out by a manufacturer-certified installer in accordance with the conditions and limitations of this Report and the manufacturer’s installation instructions.
This evaluation is based on demonstrated conformance with the following criteria:
|Criteria number||Criteria name|
|CCMC-TG-072123.06-15||Technical Guide for Loose-Fill Cellulose Insulation System for Walls/Ceilings|
The measured densities ranged from 45 kg/m3 to 52 kg/m3 in walls and from 43 kg/m3 to 44 kg/m3 in ceilings. The density of the applied product in walls was determined on wall sections using 89-mm-deep and 140-mm-deep studs spaced at 400 mm and 600 mm. Ceiling densities were determined on roof sections containing 254-mm-deep rafters and 355-mm-deep trusses spaced at 600 mm.
The thermal resistance was measured on samples with densities ranging from 48.0 to 51.24 kg/m3 and the respective thermal resistance per unit thickness ranged from 25.4 (m2·K/W)/m to 25.9 (m2·K/W)/m. Using 25.4 (m2·K/W)/m for design calculations, the thermal resistance of the insulation is 3.56 m2·K/W for a 140-mm-thick wall and 2.26 m2·K/W for an 89-mm-thick wall.
This evaluation is issued by the Canadian Construction Materials Centre (CCMC), a part of the Construction Research Centre at the National Research Council of Canada (NRC). The evaluation must be read in the context of the entire CCMC Registry of Product Assessments and the legislated applicable building code in effect.The CCMC was established in 1988 on behalf of the applicable regulator (i.e., the provinces and territories) to ensure—through assessment—conformity of alternative and acceptable solutions to regional building codes as determined by the local authority having jurisdiction (AHJ) as part of the issuance of a building permit.
It is the responsibility of the local AHJs, design professionals, and specifiers to confirm that the evaluation is current and has not been withdrawn or superseded by a later issue. Please refer to the website or contact:
Canadian Construction Materials Centre
Construction Research Centre
National Research Council of Canada
1200 Montreal Road
Ottawa, Ontario, K1A 0R6
The NRC has evaluated the material, product, system or service described herein only for those characteristics stated herein. The information and opinions in this evaluation are directed to those who have the appropriate degree of experience to use and apply its contents (i.e., AHJs, design professionals and specifiers). This evaluation is only valid when the product is installed in strict compliance with the stated conditions and limitations of evaluation and the applicable local building code. In circumstances where no applicable local building permit is issued and that no confirmation of compliance ‘for use in the intended field application’ is undertaken, this evaluation is null and void in all respects. This evaluation is provided without representation, warranty, or guarantee of any kind, expressed, or implied, and the NRC provides no endorsement for any evaluated material, product, system or service described herein. The NRC accepts no responsibility whatsoever arising in any way from any and all use and reliance on the information contained in this evaluation with respect to its compliance to the referenced code(s) and standard(s). The NRC is not undertaking to render professional or other services on behalf of any person or entity nor to perform any duty owed by any person or entity to another person or entity.
Une version française de ce document est disponible.
In the case of any discrepancy between the English and French version of this document, the English version shall prevail.
© 2021 Her Majesty the Queen in Right of Canada, as represented by the National Research Council of Canada.
All rights reserved. No part of this publication may be reproduced, stored in a retrieval system, or transmitted in any form or by any means, electronic, mechanical, photocopying, recording or otherwise, without the prior written permission of the CCMC.