[CCMC 11170-L] CCMC Standard compliance evaluation
From: National Research Council Canada
Quali-T-Fab Division de Quali-T-Groupe ULC
24, rue du Pacifique Est
In most jurisdictions this document is sufficient evidence for approval by Canadian authorities.Learn more about CCMC recognition Look for the trusted CCMC mark on products to verify compliance.
- Quali-T-Fab – Model 2436
- Quali-T-Fab – Model 3050
- Quali-T-Fab – Model 5080
- Quali-T-Fab – Model 6090
The product is a telescopic, adjustable, double-tubed steel column. The main dimensions of each model are shown in following table.
|Model||Outer tube||Inner tube|
|Outer diameter (mm)||Wall thickness (mm)||Outer diameter (mm)||Wall thickness (mm)|
The product is mounted with a 24-mm adjustable screw unit. The top and bottom plates are manufactured in several shapes and dimensions that meet the minimum requirements of CAN/CGSB-7.2.
This evaluation is valid only for products produced at the following plant:
|Product names||Manufacturing plant|
|Bromont, QC, CA|
|Quali-T-Fab – Model 2436||Product evaluated by the CCMC|
|Quali-T-Fab – Model 3050||-|
|Quali-T-Fab – Model 5080||-|
|Quali-T-Fab – Model 6090||-|
Product evaluated by the CCMC Indicates that the product from this manufacturing facility has been evaluated by the CCMC
This evaluation is based on demonstrated conformance with the following criteria:
|Criteria number||Criteria name|
|CAN/CGSB-7.2-94, Type 1||Adjustable Steel Columns|
The maximum extension and the maximum allowable load for each model are shown in the following table.
|Model||Maximum extension (mm)||Maximum allowable loadTable footnote (1) (kN)|
Use of Canadian Construction Materials Centre (CCMC) assessments
This assessment must be read in the context of the entire CCMC Registry of Product Assessments, any applicable building code or by-law requirements, and/or any other regulatory requirements (for example, the Canada Consumer Product Safety Act, the Canadian Environmental Protection Act, etc.).
It is the responsibility of the user to confirm that the assessment they are using is current and has not been withdrawn or superseded by a later version on the CCMC Registry of Product Assessments.
The National Research Council of Canada (NRC) has evaluated only the characteristics of the specific product described herein. The information and opinions in this evaluation are directed to those who have the appropriate degree of experience to use and apply its contents (such as authorities having jurisdiction, design professionals and specifiers). This evaluation is valid when the product is used as part of permitted construction, respecting all conditions and limitations stated in the evaluation, and in accordance with applicable building codes and by-laws.
This evaluation is provided without representation, warranty or guarantee of any kind, expressed or implied, and the NRC provides no endorsement for any evaluated product. The NRC accepts no responsibility whatsoever arising in any way from any and all use of or reliance on the information contained herein or the use of any evaluated product. The NRC is not undertaking to render professional or other services on behalf of any person or entity nor to perform any duty owed by any person or entity to another person or entity.
Une version française de ce document est disponible.
In the case of any discrepancy between the English and French version of this document, the English version shall prevail.
© His Majesty the King in Right of Canada, as represented by the National Research Council of Canada, 2023
All rights reserved. No part of this publication may be reproduced, stored in a retrieval system, or transmitted in any form or by any means, electronic, mechanical, photocopying, recording or otherwise, without the prior written permission of the CCMC.