[CCMC 09799-L] CCMC Standard compliance evaluation
From: National Research Council Canada
|Product name:||CertainTeed Blowing Insulation|
In most jurisdictions this document is sufficient evidence for approval by Canadian authorities.Learn more about CCMC recognition
Product nameCertainTeed Blowing Insulation
Product descriptionThe product is a mineral fibre thermal building insulation that is made from glass fibre. The product is designed for pneumatic application using commercially available blowing equipment.
This evaluation is limited to products produced at the following plant(s):
- Ottawa, Ontario, Canada
- Redcliff, Alberta, Canada
This evaluation is based on demonstrated conformance with the following criteria:
|Criteria number||Criteria name|
|CAN/ULC-S702-09, Type: 5||Standard for Mineral Fibre Thermal Insulation for Buildings|
The declared thermal resistance value is 19.0 (m2·KW)/m at a design density of 12.3 kg/m3. This product must be installed in unconfined spaces with slopes not exceeding 4.5:12 and according to the following application chart.
|Minimum settled thickness
|Minimum mass per unit area
|Maximum net coverage per 15‑kg bag
This evaluation is issued by the Canadian Construction Materials Centre (CCMC), part of the Construction Research Centre at the National Research Council of Canada (NRC). The evaluation must be read in the context of the entire CCMC Registry of Product Assessments and the legislated applicable building code in effect.
The CCMC was established in 1988 on behalf of the applicable regulator (i.e., the provinces and territories) to ensure—through assessment—conformity of alternative and acceptable solutions to regional building codes as determined by the local authority having jurisdiction (AHJ) as part of the issuance of a building permit.
It is the responsibility of the local AHJs, design professionals, and specifiers to confirm that the evaluation is current and has not been withdrawn or superseded by a later issue. Please refer to the website or contact:
Canadian Construction Materials Centre
Construction Research Centre
National Research Council of Canada
1200 Montreal Road
Ottawa, Ontario, K1A 0R6
The NRC has evaluated the material, product, system or service described herein only for those characteristics stated herein. The information and opinions in this evaluation are directed to those who have the appropriate degree of experience to use and apply its contents (i.e., AHJs, design professionals and specifiers). This evaluation is only valid when the product is installed in strict compliance with the stated conditions and limitations of evaluation and the applicable local building code. In circumstances where no applicable local building permit is issued and that no confirmation of compliance ‘for use in the intended field application’ is undertaken, this evaluation is null and void in all respects. This evaluation is provided without representation, warranty, or guarantee of any kind, expressed, or implied, and the NRC provides no endorsement for any evaluated material, product, system or service described herein. The NRC accepts no responsibility whatsoever arising in any way from any and all use and reliance on the information contained in this evaluation with respect to its compliance to the referenced code(s) and standard(s). The NRC is not undertaking to render professional or other services on behalf of any person or entity nor to perform any duty owed by any person or entity to another person or entity.
Une version française de ce document est disponible.
In the case of any discrepancy between the English and French version of this document, the English version shall prevail.
© 2021 Her Majesty the Queen in Right of Canada, as represented by the National Research Council of Canada.
All rights reserved. No part of this publication may be reproduced, stored in a retrieval system, or transmitted in any form or by any means, electronic, mechanical, photocopying, recording or otherwise, without the prior written permission of the CCMC.