[CCMC 14102-R] CCMC Canadian code compliance evaluation
From: National Research Council Canada
In most jurisdictions this document is sufficient evidence for approval by Canadian authorities.Learn more about CCMC recognition Look for the trusted CCMC mark on products to verify compliance.
It is the opinion of the Canadian Construction Materials Centre that the evaluated products, when used as sheathing membranes installed over DensGlass® exterior gypsum sheathing in accordance with the conditions and limitations stated in this evaluation, comply with the following code:
National Building Code of Canada 2015
|ID||Code provision||Solution type|
|05-01-04-01-05-0-00||188.8.131.52.(5).(a) By design complying with Subsection 5.2.2, for individual app ...||Acceptable|
|05-01-04-02-01-b-01||184.108.40.206.(1)(b)(i) Resistance to Deterioration||Acceptable|
|05-01-04-02-01-b-02||220.127.116.11.(1)(b)(ii) Resistance to Deterioration (i.e., degradation due to condensation)||Acceptable|
|05-06-02-01-00-0-00||18.104.22.168.(1) Except as provided in Sentence 22.214.171.124.( ...||Acceptable|
|09-25-05-01-00-0-00||126.96.36.199.(1) Except as provided in Sentences 188.8.131.52 ...||Acceptable|
|09-27-02-01-00-0-00||184.108.40.206.(1) Except where exterior walls are protecte ...||Acceptable|
|09-27-02-03-01-b-00||220.127.116.11.(1)(b) An open drainage material, not less tha ...||Acceptable|
|09-27-02-03-01-c-00||18.104.22.168.(1)(c) The cladding is loosely fastened to the backing and ...||Acceptable|
|09-27-03-02-00-0-00||22.214.171.124. Sheathing Membrane Material Standard||Alternative|
|09-27-03-03-00-0-00||126.96.36.199.(2) Sheathing membrane required in Sentence ...||Alternative|
The above opinion(s) is/are based on the evaluation by the CCMC of technical evidence provided by the evaluation holder, and is bound by the stated conditions and limitations. For the benefit of the user, a summary of the technical information that forms the basis of this evaluation has been included.
- Si-COAT® 421AB™ – Liquid-Applied Sheathing Membranes
- Si-COAT® 420AB™ – Liquid-Applied Sheathing Membranes
- Si-COAT® 422AB™ – Liquid-Applied Sheathing Membranes
Si-COAT® 420AB™, 421AB™, and 422AB™ sheathing membranes are identified by CSL Silicones Inc. as an assembly of proprietary silicone-based component materials for sealing installed DensGlass® exterior gypsum wall sheathing(1). The products are spray-applied liquid silicone that are moisture-cured, elastomeric and monolithic, and form a membrane that resists moisture and protects against air infiltration. Si-COAT® 420AB™ is the base product, Si-COAT® 421AB™ is for cold-weather applications and Si-COAT® 422AB™ is a low volatile organic compound (VOC) formulation.
The products are sprayed on-site by CSL Silicones Inc.-approved installers certified by The Society for Protective Coatings (SSPC). The coatings are to be spray-applied to have a target dry film thickness (DFT) of 0.62 ± 0.13 mm (25 ± 5 mils). To achieve this thickness when dry, the coatings must be installed at a specific target wet film thickness (WFT). For the Si-COAT® 420AB™ and 421AB™ products, the WFT range is 0.76 to 1.14 mm (30 to 45 mils) to produce a DFT of 0.62 ± 0.13 mm (25 ± 5 mils), while the Si-COAT® 422AB™ product is to be sprayed to a WFT range of 0.64 to 0.88 mm (25 to 35 mils) to produce a DFT of 0.62 ± 0.13 mm (25 ± 5 mils). The cured coating forms a silver/grey silicone membrane; however, additional colours are also available.
Before the final overall coating is sprayed by the SSPC-certified installer, the joints and fastener heads in the DensGlass® gypsum sheathing substrate are to be sealed with CSL423 Liquid-Applied Air Barrier(2) Flashing Sealant or CSL424 Weatherproofing Sealant, which are applied in a serpentine fashion and then spread to form a 100 mm (4 in.) ribbon over the joint having a WFT of 0.635 mm (25 mils). The rough openings of windows and doors are to be flashed with the CSL423 Liquid-Applied Air Barrier Flashing Sealant. All applications must be in accordance with the CSL installation instructions specified below.
Scope of evaluation
Sheathing membrane function
This product evaluation is to qualify the proprietary Si-COAT® 420™, 421AB™, and 422AB™ liquid-applied membranes and sealant accessories as the designated sheathing membrane serving as the inner boundary(3) of the required second plane of protection from precipitation.
Substrates and required insulation
As per the test results in the Technical evidence section of this Report, the products are semi-vapour permeable and provide a breather-type performance when installed at the specified WFT over 12.5-mm DensGlass®. The combined water vapour permeance (WVP) is 187-251 ng/(Pa·s·m2), which is above the 60 ng/(Pa·s·m2) requirement. Therefore, no insulation is required, but it may be installed to improve the thermal resistance of the wall assembly.
The products and CSL-specified sealant accessories shall be installed in accordance with the CSL Silicones Inc. publication, “Si-COAT® 420AB™, 421AB™, 422AB™, Liquid-Applied Sheathing Membranes: Application Instructions for Building Envelope Solutions” dated 18-05-2018. The CSL-authorized installers are trained and certified installers by SSPC. The card-carrying SSPC installers shall have their certification cards on hand and a copy of the CSL installation instructions on-site for review by the building officials during their inspection. The WFT gauge shall be used to confirm that the film thickness is within the target limits of 25 ± 5 mils. (Extracts from the installation instructions are shown in figure "Typical application of CSL423 Liquid-Applied Air Barrier Flashing Sealant and CSL424 Weatherproofing Sealant where specified to maintain continuity against rain penetration" for information purposes only. See figure "CSL Silicones wet film thickness gauge" for the specified WFT gauge.)
This evaluation is valid only for products produced at the following plant:
|Product names||Manufacturing plant|
|Guelph, ON, CA|
|Si-COAT® 421AB™ – Liquid-Applied Sheathing Membranes||Product evaluated by the CCMC|
|Si-COAT® 420AB™ – Liquid-Applied Sheathing Membranes||Product evaluated by the CCMC|
|Si-COAT® 422AB™ – Liquid-Applied Sheathing Membranes||Product evaluated by the CCMC|
Product evaluated by the CCMC Indicates that the product from this manufacturing facility has been evaluated by the CCMC
Conditions and limitations
The CCMC’s compliance opinion is bound by this product being used in accordance with the conditions and limitations set out below.
- Following the relevant limitations related to the proper installation of the products in conformance with the CSL-specified installation instructions entitled, “Si-COAT® 420AB™, 421AB™, 422AB™, Liquid-Applied Sheathing Membranes: Application Instructions for Building Envelope Solutions,” dated 18/05/2018.
- The installation must be conducted by SSPC-certified installers to ensure the DFT is installed within the specified target of 25 ± 5 mils by ensuring that the target wet film thicknesses are not exceeded using the film thickness gauge shown in figure "CSL Silicones wet film thickness gauge". The manufacturer should be contacted if the installation does not conform to the CSL specifications.
- All exterior wall penetrations must be sealed with the specified CSL sealant as per the CSL instructions before the Si-COAT® coatings are installed over the entire surface.
- If the DFT is excessively over-spec (i.e., > specified 30 mils), the WVP may be below 60 ng/(Pa·s·m2), and insulation must then be installed to comply with the outboard/inboard ratio specified in Article 188.8.131.52 of Division B of the NBC 2015.
- The cladding fasteners must be installed at stud locations as exterior gypsum sheathing is not approved as a cladding attachment.
- The components must be clearly identified with the phrase “CCMC 14102-R".
This evaluation is based on demonstrated conformance with the following criteria:
|Criteria number||Criteria name|
|CCMC-TG-072510.14-15||CCMC Technical Guide for Liquid-Applied Coating as Sheathing Membrane|
The Report Holder has submitted technical documentation for the CCMC’s evaluation. Testing was conducted at laboratories recognized by the CCMC in accordance with the CCMC's Technical Guide for Liquid-Applied Silicone-Based Sheathing Membranes over DensGlass® Exterior Gypsum Sheathing. The corresponding technical evidence for this product is summarized below.
|Tensile elongation||%||Report value||251||175||125|
|After UV aging||%||≥ 90% original value||228||201||176|
|After UV and heat aging||%||≥ 85% original value||296||224||215|
|Water vapour permeance||ng/(Pa·s·m2)||> 60||236||251||187|
|Water absorption coefficient (WAC)||mg/(m2∙s1/2)||< 4 000Table footnote footnote (2)||87||140||146|
|Water penetration at fastenersTable footnote footnote (3)||g||Water penetration must be ≤ that of the benchmark||Pass||Pass||Pass|
|Membrane adhesion||Substrate conditioning||Unit||Requirement||Si-COAT® results|
|DensGlass®Table footnote (1)||oven dry||kPa||
Panel failure (report strength) adhesive failure area must be below 5%
|78||107||59||All specimens passed maximum 5% failed area criterion|
|50% relative humidity||163||123||134|
|Joint disruption resistance (single-point load bending)||n/a||No cracking, debonding, delamination or other deleterious effects at a deflection of L/180||Pass||Pass||Pass|
|Report load (kN) at 13.5 mm deflection||6.0 kN||6.0 kN||5.8 kN|
|Water vapour permeance after UV and heat aging||ng/(Pa·s·m2)||> 60Table footnote (1)||201||161||177|
|Water absorption coefficient (WAC) after UV and heat aging||mg/(m2∙s1/2)||< 4 000Table footnote (2)||161||150||163|
Use of Canadian Construction Materials Centre (CCMC) assessments
This assessment must be read in the context of the entire CCMC Registry of Product Assessments, any applicable building code or by-law requirements, and/or any other regulatory requirements (for example, the Canada Consumer Product Safety Act, the Canadian Environmental Protection Act, etc.).
It is the responsibility of the user to confirm that the assessment they are using is current and has not been withdrawn or superseded by a later version on the CCMC Registry of Product Assessments.
The National Research Council of Canada (NRC) has evaluated only the characteristics of the specific product described herein. The information and opinions in this evaluation are directed to those who have the appropriate degree of experience to use and apply its contents (such as authorities having jurisdiction, design professionals and specifiers). This evaluation is valid when the product is used as part of permitted construction, respecting all conditions and limitations stated in the evaluation, and in accordance with applicable building codes and by-laws.
This evaluation is provided without representation, warranty or guarantee of any kind, expressed or implied, and the NRC provides no endorsement for any evaluated product. The NRC accepts no responsibility whatsoever arising in any way from any and all use of or reliance on the information contained herein or the use of any evaluated product. The NRC is not undertaking to render professional or other services on behalf of any person or entity nor to perform any duty owed by any person or entity to another person or entity.
Une version française de ce document est disponible.
In the case of any discrepancy between the English and French version of this document, the English version shall prevail.
© His Majesty the King in Right of Canada, as represented by the National Research Council of Canada, 2023
All rights reserved. No part of this publication may be reproduced, stored in a retrieval system, or transmitted in any form or by any means, electronic, mechanical, photocopying, recording or otherwise, without the prior written permission of the CCMC.