[CCMC 13253-R] CCMC Canadian code compliance evaluation
From: National Research Council Canada
EIDCA Specialty Products Company (company of DuPont)
6925 Century Avenue, Suite 700
Tyvek® CommercialWrap® – Air Barrier Material™
|Compliance:||NBC 2015, OBC|
In most jurisdictions this document is sufficient evidence for approval by Canadian authorities.Learn more about CCMC recognition Look for the trusted CCMC mark on products to verify compliance.
It is the opinion of the Canadian Construction Materials Centre that the evaluated product, when used as an air barrier material in accordance with the conditions and limitations stated in this evaluation, complies with the following code:
National Building Code of Canada 2015
|ID||Code provision||Solution type|
|05-04-01-02-00-0-00||22.214.171.124.(1) Except as provided in Sentence 126.96.36.199.( ...||Acceptable|
|09-25-03-02-00-0-00||188.8.131.52.(2) Where polyethylene sheet is used to prov ...||Alternative|
|09-36-02-10-00-0-00||184.108.40.206.(1) Materials intended to provide the princi ...||Acceptable|
Ontario Building Code
Ruling No. 11-12-270 (13253-R) authorizing the use of this product in Ontario, subject to the terms and conditions contained in the Ruling, was made by the Minister of Municipal Affairs and Housing on 2011-11-22 (revised 2023-05-23) pursuant to s.29 of the Building Code Act, 1992 (see Ruling for terms and conditions). This Ruling is subject to periodic revisions and updates.
The above opinion(s) is/are based on the evaluation by the CCMC of technical evidence provided by the evaluation holder, and is bound by the stated conditions and limitations. For the benefit of the user, a summary of the technical information that forms the basis of this evaluation has been included.
Tyvek® CommercialWrap® – Air Barrier Material™
This evaluation addresses the performance of the product as an air barrier material within the DuPont Canada-specified Tyvek® CommercialWrap® air barrier system. The DuPont Canada-specified Tyvek® CommercialWrap® air barrier system has not been evaluated, but is covered in the Additional information section of this evaluation for the convenience of building officials and designers.
If the product is installed as part of the designated air barrier system, it will serve a dual function in the wall assembly. Use of the product as a sheathing membrane to control incidental water infiltration behind cladding is covered under a separate CCMC evaluation (see CCMC 13119-R).
The product is made by flash spinning fibres of high-density polyolefin, then combining and bonding the fibres into a sheet using heat and pressure. Antioxidants and ultraviolet stabilizers are compounded into the polyolefin resin before spinning. The product is white and is 0.20 mm thick. The product is available in rolls that are 3.05 m wide × 38.10 m long or 1.53 m wide × 60.96 m long.
This evaluation is valid only for products produced at the following plant:
|Product name||Manufacturing plant|
|Richmond, VA, US|
|Tyvek® CommercialWrap® – Air Barrier Material™||Product evaluated by the CCMC|
Product evaluated by the CCMC Indicates that the product from this manufacturing facility has been evaluated by the CCMC
Conditions and limitations
The CCMC’s compliance opinion is bound by this product being used in accordance with the conditions and limitations set out below.
- When the product is installed as part of the main airtight element in the designated air barrier system, the vapour barrier needs only to comply with Article220.127.116.11., Vapour Barrier Materials, of Division B of the NBC 2015 (i.e. does not need to be continuous but must meet the maximum 60 ng/(Pa∙s∙m2) requirements and the other applicable requirements of this Article). In cases where another low air and water vapour permeance material has been installed outboard of the innermost impermeable surface of the assembly, then Article18.104.22.168., General (Properties and Position of Materials in the Building Envelope), of Division B of the NBC 2015 must be met.
- The product must be installed:
- with the printed side facing outward and protected from exposure to ultraviolet (UV) radiation from the sun within 60 days;
- with a minimum 10-mm air space between the sheathing membrane and the cladding, unless the cladding has been deemed to not require an air space (e.g., deemed by the CCMC or by building officials based on past cladding performance); and
- according to DuPont™ Tyvek® Sheathing Membranes and DuPont Self-Adhered Flashing Products Installation Guidelines dated October 2022 (sheathing membrane, air barrier and header wrap). Examples of the installation details are presented in Additional information.
- A concealed air space exceeding 25 mm in width must contain proper fire blocking, in accordance with Subsection 9.10.16., Fire Blocks, of Division B of the NBC 2015.
- Where a CCMC-evaluated sheathing tape in accordance with the MasterFormat 07 25 20 is used to seal joints, the Tyvek® CommercialWrap® must be referenced as a tested substrate within the CCMC sheathing tape evaluation report otherwise, its adhesion over the Tyvek® CommercialWrap® must be validated by DuPont.
This evaluation is based on demonstrated conformance with the following criteria:
|Criteria number||Criteria name|
|CCMC-TG-072709.02-15D||CCMC Technical Guide for Air Barrier Materials|
The evaluation holder has submitted technical documentation for the CCMC’s evaluation. Testing was conducted at laboratories recognized by the CCMC. The corresponding technical evidence for this product is summarized below.
|Five 1 m2 membrane specimens tested and measured for air permeance at a minimum of six air pressure differentials (ΔP) between 0 Pa and 300 Pa||
|L/(s·m2)||Air leakage rate at 75 Pa ΔP (based on linear regression of 30 data points) ≤ 0.02||0.0008|
|conditioned specimens||N/A||Where less than 0.01 L/(s·m2) for unconditioned specimens, the air leakage rate for conditioned specimens must not increase by more than 0.001 L/(s·m2) at 75 Pa pressure difference||Pass|
|Water vapour transmission||exfiltration direction||ng/(Pa∙s∙m2)||Report Value||
|Water vapour transmission||infiltration direction||ng/(Pa∙s∙m2)||Report Value||
The assessment of the product’s durability is covered under CCMC 13119-R.
An air barrier material as part of an air barrier system
The CCMC has not evaluated the performance of the Tyvek® CommercialWrap® air barrier system as to its conformance with Article 22.214.171.124., Air Barrier System Properties, of Division B of the NBC 2015. However, the CCMC’s opinion is that an air barrier system using this material and installed in conformance with the details outlined below, as well as in conformance with DuPont™ Tyvek® Sheathing Membranes and DuPont Self-Adhered Flashing Products Installation Guidelines, should satisfy the requirements for continuity of the air barrier system in Articles 126.96.36.199., Required Barrier to Air Leakage, and 188.8.131.52., Continuity of the Air Barrier System, of Division B of the NBC 2015.
Authorities having jurisdiction (AHJ) should be aware that this system differs from the typical air barrier approach, which uses a flexible membrane as the principal plane of airtightness. In the typical approach, the membrane (i.e., polyethylene sheet) is normally sandwiched between two other materials so that it is not required to resist, on its own, the full force of indoor/outdoor pressure differences induced by stack effect, mechanical systems and, most importantly, wind.
In a system in which the membrane is applied to the outer surface of the wall sheathing, as it is in the Tyvek® CommercialWrap® air barrier system, that membrane does not have continuous support against outward air pressure. The membrane must, therefore, have adequate strength to resist that pressure by spanning between points of support, such as its own fastening points or the points where strapping or cladding is fastened to the wall. The CCMC’s evaluation of the Tyvek® CommercialWrap® material does not include the evaluation of this strength or the strength of the continuity details. The AHJ must, therefore, determine whether the product’s air barrier system, described herein, meets the intent of Sentence 184.108.40.206.(1) of Division B of the NBC 2015, as being an effective barrier for the proposed construction in the proposed geographical/climate area. For example, the AHJ may deem the proposed air barrier system adequate for buildings in urban areas, sheltered sites or areas of low wind, based on their experience, but inadequate in areas of high wind and exposed sites in rural or coastal areas.
An air barrier system checklist for the AHJ to consider is below.
An air barrier system must:
- have an acceptable low air leakage rate;
- be continuous;
- be durable;
- have sufficient strength to resist the anticipated air pressure load; and
- be buildable in the field.
The product’s material is applied over exterior wood-based wall sheathing material complying with the NBC 2015. It does not contribute to an air barrier system until it is joined to the other components that make up the air barrier system of the building. DuPont™ Tyvek® Sheathing Membranes and DuPont Self-Adhered Flashing Products Installation Guidelines outlines how the product’s material must be joined to the foundation wall, to windows and doors, to penetrations in the wall, and to the ceiling air barrier, thus forming the system.
A successful air barrier system installation is predicated on sequencing during construction. Coordination is required during erection of framing and after completion of the air barrier system to ensure that no other trade breaches the integrity of the installed air barrier system.
The proposed air barrier system is defined as possessing the following features:
- Tyvek® CommercialWrap® material as the principal plane of airtightness;
- accessories, including sealants and CCMC-evaluated sheathing tape (that has adhesion strength with Tyvek® CommercialWrap® approved by DuPont) to maintain continuity at junctions with penetrations in the wall assembly (i.e., windows, doors, pipes, ducts, electrical outlets, etc.) and in accordance with continuity details in the DuPont™ Tyvek® Sheathing Membranes and DuPont Self-Adhered Flashing Products Installation Guidelines;
- durability, meeting UV- and heat-aging requirements; and
- exterior sheathing with specified fasteners and fastening schedule of the Tyvek® CommercialWrap® for structural support against anticipated pressure loads.
The air barrier system is to be built in the field by informed builders and reviewed by building officials. DuPont Canada has established a field monitoring program to ensure the proper installation of the air barrier system.
The figures below outline typical construction details on the installation of the Tyvek® CommercialWrap® – Air Barrier Material™ air barrier system in the field. See DuPont™ Tyvek® Sheathing Membranes and DuPont Self-Adhered Flashing Products Installation Guidelines for additional details.
All horizontal joints in the material must be overlapped by at least 100 mm and taped with CCMC-evaluated sheathing tape (that has adhesion strength with Tyvek® CommercialWrap® approved by Dupont). To maintain continuity of the plane of airtightness, the material must be sealed to the roof by using an appropriate transition membrane. The material should be secured underneath the transition membrane to ensure proper shingling.
Wood-based sheathing, glass-fibre-faced exterior gypsum board, or exterior gypsum board having a water vapour permeance of less than 60 ng/(Pa·s·m2) must be installed in accordance with Article 220.127.116.11., Position of Low Permeance Materials, of Division B of the NBC 2015.
For wood-based sheathing, a gap of not less than 2 mm must be left between sheets in accordance with Article 18.104.22.168., Joints in Panel-Type Sheathing, of Division B of the NBC 2015.
Since the foundation wall is part of the air barrier system, the product must be sealed to the foundation wall to maintain the continuity of the plane of airtightness. The sealant used must be compatible with the product. For example, silicone-based sealants must not be used. To maintain watertightness, Tyvek® CommercialWrap® – Air Barrier Material™ sheathing membrane must be installed over the flashing and taped to properly drain any rain penetration breaching the cladding.
When installed as the principal plane of airtightness, the product must be structurally attached with nails with plastic washers, screws with plastic washers, or appropriate brick tie anchors.
For wood-frame construction where the sheathing is plywood, insulated board, glass-fibre-faced exterior gypsum, or exterior gypsum board, use nails with plastic washers and brick tie anchors.
For steel-framed construction where the sheathing is glass-fibre-faced exterior gypsum or exterior gypsum, use screws with washers and brick tie fasteners.
All seams require a 100-mm minimum overlap, and both vertical and horizontal seams should be secured with a CCMC-evaluated sheathing tape.
The material must be cut and wrapped around framing at openings (see Figure 4). Cut ends should then be taped or caulked to the inside frame. To ensure continuity at this junction, a seal must be established with the window or door element (see Figure 5).
The plane of airtightness of the material must be made continuous with windows and doors that are part of the air barrier system for the building envelope. The material must be sealed to the window or door frames with either sealant/backer rod or filled with sealant foam. Sealants must be compatible with the material and adhere to the framing material.
All exterior electrical boxes or other penetrations through the material must be rendered airtight to maintain the plane of airtightness of the air barrier system. All electrical boxes must be wrapped and taped to the product’s membrane, or airtight electrical boxes can be used.
Where pipes and ducts may breach the Tyvek® CommercialWrap® – Air Barrier Material™ membrane, they must be sealed to the membrane. A sealant bead compatible with the product and the pipe or duct material or CCMC-evaluated sheathing tape is recommended.
Use of Canadian Construction Materials Centre (CCMC) assessments
This assessment must be read in the context of the entire CCMC Registry of Product Assessments, any applicable building code or by-law requirements, and/or any other regulatory requirements (for example, the Canada Consumer Product Safety Act, the Canadian Environmental Protection Act, etc.).
It is the responsibility of the user to confirm that the assessment they are using is current and has not been withdrawn or superseded by a later version on the CCMC Registry of Product Assessments.
The National Research Council of Canada (NRC) has evaluated only the characteristics of the specific product described herein. The information and opinions in this evaluation are directed to those who have the appropriate degree of experience to use and apply its contents (such as authorities having jurisdiction, design professionals and specifiers). This evaluation is valid when the product is used as part of permitted construction, respecting all conditions and limitations stated in the evaluation, and in accordance with applicable building codes and by-laws.
This evaluation is provided without representation, warranty or guarantee of any kind, expressed or implied, and the NRC provides no endorsement for any evaluated product. The NRC accepts no responsibility whatsoever arising in any way from any and all use of or reliance on the information contained herein or the use of any evaluated product. The NRC is not undertaking to render professional or other services on behalf of any person or entity nor to perform any duty owed by any person or entity to another person or entity.
Une version française de ce document est disponible.
In the case of any discrepancy between the English and French version of this document, the English version shall prevail.
© His Majesty the King in Right of Canada, as represented by the National Research Council of Canada, 2023
All rights reserved. No part of this publication may be reproduced, stored in a retrieval system, or transmitted in any form or by any means, electronic, mechanical, photocopying, recording or otherwise, without the prior written permission of the CCMC.